Natatorium Building Enclosure Deterioration Due to Moisture Migration
AbstractThe natatorium enclosure at the Avon Recreation Center in Avon, Colorado experienced significant deterioration of the CMU façade due to moisture carried by humid air from the interior of the space into the wall assembly. This situation was caused by a combination of an insufficient interior air and vapor barrier along with an HVAC system that failed to provide negative pressurization to the space. This case study describes the investigation carried out to determine the causes of wall and roof deterioration at the building, and details the repair efforts undertaken. Lessons learned are presented to help designers, building owners, and maintenance personnel prevent similar problems from occurring in their buildings.
Scifeed alert for new publicationsNever miss any articles matching your research from any publisher
- Get alerts for new papers matching your research
- Find out the new papers from selected authors
- Updated daily for 49'000+ journals and 6000+ publishers
- Define your Scifeed now
Graham, L.; Scott, M.; Pappas, A. Natatorium Building Enclosure Deterioration Due to Moisture Migration. Buildings 2012, 2, 534-541.
Graham L, Scott M, Pappas A. Natatorium Building Enclosure Deterioration Due to Moisture Migration. Buildings. 2012; 2(4):534-541.Chicago/Turabian Style
Graham, Lawrence; Scott, Mark; Pappas, Aleka. 2012. "Natatorium Building Enclosure Deterioration Due to Moisture Migration." Buildings 2, no. 4: 534-541.